The site above suffered from poor efficiency with an uncorrected power factor of 0.80pf (80% inefficient) and attracted reactive power charges, a penalty for inefficient users.
Annual Savings Achieved
- 7.97 tons CO2
- 50,638 kW/h site
- 80,307 kW/h inc transmission
- 7 Months
- Electrical efficiency improved from 80% – 98%
- Removal of reactive power charges
- Reduction of 271 amps per phase
- Reduction of 195 kVa demand
- Improved utility
Their main criteria was to reduce energy costs and improve the overall electrical efficiency of the site while maintained a short return on investment.
Our equipment returned a payback of seven months.
The project included the supply and install of new equipment to achieve and overall electrical efficiency of around 99% from a poor 80% before correction.
For more information on how EnergyAce can benefit your organisation, call us now on 01695 559785 or email email@example.com.
Download Case Study